There is currently no cabinet in our village, we are fed from a PCP around 5km away . From the existing cabinet outwards, there are approx 150 to 160 properties. We are approx 7.5km in total from the exchange and get around 2 to 3Mb down so that suggests we may be on thicker than standard conductors.
Looking at the cable specs link a 100 pair 0.6mm dia conductor is around 62.5mm outer diameter which would make sense and I understand there are two cables feeding our village, one down either side of the road. It would make sense in that if the original duct was 90mm and already had a 62.5mm cable in it, they had to run in a new duct/cable as another 62.5mm cable wouldnt fit in that original duct.
The cable certainly looked like it took up a lot of the existing duct and at 90mm duct ID less 62.5mm OD cable that only leaves ~27.5mm which would be too tight for running one of their "standard" 25mm fibre ducts, hence the new third 90mm duct being laid.
Zen Unlimited Fibre Office BQM