If what is true? William's statement, which clearly is not, or MtSaffron's?
The distance from the cabinet for attenuation estimation has always been cabling premises to PCP plus cabling from PCP to FTTC cabinet. Note only one length between the cabinets, not the two that are used.
This is why Openreach want the two cabinets as close as possible. Fifty metres is the preferred maximum, not a target distance.
Kindness isn't going to cure the world of all its awfulness but it's a good place to begin. Daisy Ridley.
My broadband basic info/help site - www.robertos.me.uk.
Domains, site and mail hosting - Tsohost
Connection - AAISP Home::1 80/20. Sync 54999/14466Kbps @ 600m. BQMs - IPv4